Correct use of purchase argon gas
1, Before using argon, adjust the argon tank pressure to 0.8-1.2MPa, open the argon gas meter, make the pressure reach 0.18-0.25Mpa, meet the requirements of all pipeline connection equipment, the argon gas pressure Control in a stable position.
2, during the use of the process, each shift should check the tank pressure, when the pressure is close to the upper and lower limits of the use of equipment, reach or close to the minimum reserves of argon tanks, to increase the frequency of observations, and timely reporting, for replacement.
3. Pressurization operation: When the storage tank pressure is close to the lower limit of the equipment use requirement, the booster valve is started to pressurize. The operation procedure is: slowly open the pressure booster valve, when the pressure gauge of the storage tank indicates the normal working pressure of the equipment and low At the maximum working pressure of the tank, close the pressure booster valve.
4, during use, always observe the tank's liquid level, when the liquid level is lower than the red line, close the tank regulator, stop using argon in the tank to ensure the purity of argon gas when refilled.
5. During the use of argon gas, when the liquid is drained or there is a leakage failure, the skin is prohibited from directly contacting the liquid argon to prevent frostbite.
6, When clearing the frost of pipelines and carburetors, it cannot be strongly impacted to prevent pipeline deformation, leakage, and seal failure.
7. It is forbidden to perform hard impact, cutting, drilling, welding and other operations on the outer shell of the argon tank to prevent damage to the vacuum of the tank.
Looking forward to your inquiry for this gas welding argon purchase argon gas